To promote occupants’ productivity, comfort, and well-being by providing quality thermal comfort.
Meet the requirements for both thermal comfort design and thermal comfort control.
Thermal Comfort Design
Option 1. ASHRAE Standard 55-2017
Design heating, ventilating, and air-conditioning (HVAC) systems and the building envelope to meet the requirements of ASHRAE Standard 55–2017, Thermal Comfort Conditions for Human Occupancy with errata or a local equivalent.
For natatoriums, demonstrate compliance with ASHRAE HVAC Applications Handbook, 2015 edition, Chapter 5, Places of Assembly, Typical Natatorium Design Conditions, with errata.
Option 2. ISO Standards
Design HVAC systems and the building envelope to meet the requirements of the applicable standard:
- ISO 7730:2005, Ergonomics of the Thermal Environment, analytical determination and interpretation of thermal comfort, using calculation of the PMV and PPD indices and local thermal comfort criteria; and
- ISO 17772-2017, Energy Performance of Buildings- Indoor environmental quality- Part 1. Indoor environmental input parameters for the design and assessment of energy performance of buildings Section A2.
Thermal Comfort Control
Provide individual thermal comfort controls for at least 50% of individual occupant spaces. Provide group thermal comfort controls for all shared multioccupant spaces.
Thermal comfort controls allow occupants, whether in individual spaces or shared multioccupant spaces, to adjust at least one of the following in their local environment: air temperature, radiant temperature, air speed, and humidity.
© Copyright U.S. Green Building Council, Inc. All rights reserved.