To reduce the environmental and economic harms of excessive energy use by achieving a minimum level of energy efficiency for the building and its systems.
Option 1. Tenant-level energy simulationDemonstrate a 3% improvement in the proposed performance rating compared with the baseline performance rating for portions of the building within the tenant’s scope of work. Calculate the baseline according to ANSI/ASHRAE/IESNA Standard 90.1–2010, Appendix G, with errata (or a USGBC-approved equivalent standard for projects outside the U.S.), using a simulation model for all tenant project energy use. Projects must meet the minimum percentage savings before application of renewable energy systems. The proposed design must meet the following criteria:
- Compliance with the mandatory provisions of ANSI/ASHRAE/IESNA Standard 90.1–2010, with errata, (or a USGBC-approved equivalent standard for projects outside the U.S.);
- Inclusion of all energy consumption and costs within and associated with the tenant project; and
- Comparison against a baseline tenant project that complies with Standard 90.1–2010, Appendix G, with errata but without addenda (or a USGBC-approved equivalent standard for projects outside the U.S.).
Option 2. Prescriptive complianceComply with the mandatory and prescriptive provisions of ANSI/ASHRAE/IESNA Standard 90.1–2010, with errata (or a USGBC-approved equivalent standard for projects outside the U.S.).
- Reduce connected lighting power density by 5% below ASHRAE 90.1-2010 using the space-by-space method or by applying the whole-building lighting power allowance to the entire tenant space.
- Install ENERGY STAR appliances, office equipment, electronics, and commercial food service equipment (HVAC, lighting, and building envelope products are excluded) for 50% (by rated-power) of the total ENERGY STAR eligible products in the project. Projects outside the U.S. may use a performance equivalent to ENERGY STAR.
Alternative Compliance Paths (ACPs)
Canada ACP - NECBProjects in Canada may instead demonstrate a percentage improvement in the proposed building performance rating compared with the baseline according to the National Energy Code for Buildings (NECB) 2011. The same percentage cost improvement in energy performance is required to meet the Prerequisite, and the same points for cost percentage improvement in energy performance are applicable for the Credit. The following conditions (where applicable) must be met. Note that unless otherwise noted, CanQUEST (the Canadian energy modelling software based on eQUEST that performs NECB 2011 compliance runs) does not implement many of these conditions correctly and would require corresponding modifications to the Reference case.
- Comply with mandatory requirements of ASHRAE 90.1-2010 ASHRAE 90.1-2010 mandatory requirements must be met, in addition to the performance path limitations referenced in the NECB 2011 Sections 22.214.171.124, 126.96.36.199 and 188.8.131.52. In cases where ASHRAE and the NECBC reference requirements concerning the same item, the more stringent requirement shall be adhered to. The following exceptions apply:
- ASHRAE 90.1-2010 mandatory items 184.108.40.206, 220.127.116.11b, 18.104.22.168, 22.214.171.124, 9.4.3
- Option 1, Path 1 - Do not apply ASHRAE 90.1-2010 requirements for purchased heating and cooling. Under this ACP, purchased heating and cooling (as applicable) are modeled as cost-neutral in the baseline and proposed case. Local rates for purchased heating (fossil fuel based) and cooling are used to establish the purchased heating and cooling costs. The energy model's scope accounts for only downstream equipment, plus purchased heating and cooling. NECB clause 126.96.36.199 does not apply for LEED projects.
- Model baseline systems in accordance with NECB requirements, with DX coils replaced with chilled water coils if purchased cooling is present and fossil-fired furnaces replaced with hot water coils if purchased heating is present.
- Option 1, Path 2: Do not apply ASHRAE 90.1-2010 requirements for baseline systems. Model baseline systems in accordance with NECB requirements for onsite generated equipment (i.e. assume building is not connected to a DES and the proposed building is modeled with a virtual plant according to LEED v4 Reference Guide requirements).
© Copyright U.S. Green Building Council, Inc. All rights reserved.